The Model 110 Oil Lever Gate Valve is used in fuel oil piping systems to provide automatic shut-off of the fuel flow in the event of a fire.
Fire safety valves are required by many building and fire safety codes to be installed upstream of diesel generators, boilers, and downstream of many fuel storage tanks. The Preferred Model 110 Oil Lever Gate Valve is designed to be located in a horizontal pipe run where the oil supply enters the building, and/or at each point of use, or where dictated by code. The trip wire with fusible link is installed in the area(s) to be monitored for excess temperature.
**Additional Link Kits are only sold with the purchase oil lever gate valves.
The Model 110 Oil Lever Gate Valve is used in fuel oil piping systems to provide automatic shut-off of the fuel flow in the event of a fire. Valve operation is fully mechanical and is independent of the electrical power supply. The emergency fuel line shut-off is mandated by many codes. The assembly consists of a 125 lb. screwed full-ported bronze body and disc, lever operated quick closing mechanism with zinc plated malleable iron lever, cadmium plated steel spring, hand lapped seats and discs, and an extra long stem packing to avoid suction line air leaks. Standard installation kit includes 25' coil of wire and two (2) 165° F fusible links. **Additional links and longer wire are available upon request. The Valve can also be equipped with an automatic fuel shut-off limit switch assembly. This switch is then wired to the Fuel Oil Management System to provide “Fire” and “Loss of Fuel Supply” alarms and interlock fuel oil pump set operation.
The Model 110 Oil Lever Gate is designed to be located in a horizontal pipe run where the oil supply enters the building, and/or at each point of use, or where dictated by code. Install the trip wire with the fusible link(s) in the area(s) to be monitored for excess temperature.
Operation: The precision ground metal gate is lever operated with a quarter turn required for opening or closing. The valve is held open by a stretched wire containing one or more fusible links. When the temperature at any fusible link rises above 165° F, the link will melt and the tension of the integral spring will close the valve. NOTE: On applications utilizing long wire runs with many fusible links, a weight should be added to ensure that the valve will close reliably and quickly.
Testing: As with any piece of safety equipment, the lever gate valve should be tested upon completion of installation and regularly thereafter to ensure that it will close in the event of excess temperatures. Ideally, the link furthest from the valve would be heated with a small flame until the link melts. If the valve does not snap closed properly, the wire should be checked for freedom of movement, and the mechanism of the valve should be checked for free operation. The valve may need to be cleaned and repacked with a Teflon packing or an additional weight may need to be added.
**Additional Links are only sold with the purchase of oil lever gate valves.
|Oil Lever Gate Valve - Catalog Cutsheet|
|Oil Lever Gate Valves Installation Manual|